If you are a HECO customer and have a NEM related inquiry, please call 543-4760 or send an e-mail to firstname.lastname@example.org.
Effective December 23, 2011, all new Net Energy Metering (NEM) systems on the island of Oahu must have inverter(s) with the following frequency trip settings.
Frequency Trip Limit (Hz)
57.0 to 60.5
This change requires a single change to the inverter's operation by changing the current 59.3 Hz fast trip setting to a 57 Hz fast trip, in which the time delay remains at 0.16 second. Please consult with your solar contractor or inverter manufacturer to confirm your inverter meets the settings in the above table. The Inverter Setting Confirmation Form will need to be filled out to confirm that the inverter settings, listed in the above table have been implemented as per "Rule 14H: Interconnection of Distributed Generating Facilities in parallel with the Company's Electric System".
Learn how to read a Net Energy Meter by clicking on the video below:
Net Energy Metering (or NEM) is one way to lessen Hawaii’s dependence on imported oil by encouraging the greater use of eligible renewable energy sources like solar (photovoltaic), wind, biomass, or hydroelectric power for electrical generation by residential and commercial customers. Hawaiian Electric Company, Maui Electric Company, and Hawaii Electric Light Company support Net Energy Metering and recognize their roles to help Hawaii transition from fossil fuels to more renewable energy resources. Here is information that we hope will be helpful. For information on NEM for MECO, visit www.mauielectric.com; and for HELCO, visit www.helcohi.com.
. NEW! To learn more about the NEM program, you may download our NEW Guide to Net Energy Metering brochure by clicking here.
According to Hawaii state law (Hawaii Revised Statutes (HRS) Section 269-101 - 269-111), all residential and commercial utility customers who own and operate an eligible renewable energy generation system up to a generating capacity of 100 kW and intend to connect to utility grid, must register their systems with their utility by executing a NEM agreement. The executed agreement allows the NEM customer to connect their renewable generator to the utility grid, allowing it to export surplus electricity into the grid, and to receive credits at full retail value which can be used to offset electricity purchases over a 12-month period.
NEM customers are billed for net energy purchased, which is determined by subtracting the excess energy exported to the utility grid from the total energy supplied by the utility. Here is the formula:
NEM allows you to offset all or part of your electricity purchases from the utility by energy produced by your eligible renewable generation system and export any excess electricity to the utility grid at the retail rate.
NEM gives value to the excess electricity you produce with your renewable generation system. Electricity generated by your renewable generator would first supply power for your own needs and any additional power you need would be purchased from the utility. When a NEM customer generates more electricity than what is consumed, excess energy produced can be exported back to the utility at full retail value which can be used to offset electricity purchases over a 12-month period.
This is in contrast to other non-NEM customers with renewable energy generation systems. If they have a power purchase agreement, they are compensated for power exported to the utility grid at a lower wholesale rate. Standard interconnection customers must consume all electricity that is self-generated, and not allow to export surplus energy to the grid nor be compensated. With NEM, you are in effect being given the retail credit for excess power which you generate.
Hawaii law specifies that NEM applies to solar, wind, biomass or hydroelectric generation facilities, or a hybrid system of two or more of these technologies, with a capacity up to 100 kW. (For more information about these technologies, visit the website of the State of Hawaii, Department of Business, Economic Development and Tourism, Strategic Industries Division, Energy Branch).
The Hawaii Public Utilities Commission (PUC), by rule or order, can change the maximum allowable capacity.
4. Does a solar water heating system qualify for net energy metering?
No. NEM applies only to systems that generate electricity. Solar electric systems, known as photovoltaics (PV), use solar cells to convert the sun’s light into electricity. By contrast, solar water-heating systems use heat from the sun directly to heat water for your use. Since solar water-heating systems do not produce electricity, they cannot feed into the grid and do not qualify for NEM.
To ensure continued reliable service for all of our customers on a distribution circuit, a technical review may be needed when the amount of distributed generation (DG) on a circuit reaches 15 percent. This is not a limit on solar or other DG. The 15 percent threshold, approved by the PUC, serves as a trigger point for determining whether additional study may be needed to evaluate the impact of additional DG on the circuit. The purpose is to determine if any steps must be taken to ensure service remains reliable for all customers on that circuit when adding more DG. This is consistent with the standards used by California electric utilities.
To find out the circuit penetration level for your project, please visit the Locational Value Map (LVM) for Oahu.
6. Will I need a new meter and, if so, do I need to pay for it?
New and existing NEM systems will require a new bi-directional meter capable of measuring the energy supplied by your utility and the excess electricity from your renewable energy generation system exported to the grid. Hawaiian Electric will provide the meter at no cost to you when the NEM agreement is executed.
If you are planning to install a qualified renewable energy generation system and have an existing electric meter with a digital display, please call Hawaiian Electric at 543-4760 to confirm if your meter is compatible to ensure proper credit can be given. Your existing meter may have to be replaced before your system can be energized. If you have an existing mechanical meter, it will be replaced when the NEM agreement is executed.
All meters must be accessible by Hawaiian Electric personnel for emergencies, meter reading, inspection, testing, and maintenance in accordance with the tariff and Hawaiian Electric's Electric Service Installation Manual. For billing purposes the net meter displays more data than your current meter and needs to be manually read. Please note that upon execution (signing) of a NEM agreement, you agree to allow Hawaiian Electric personnel entry to your property during normal business hours to read and perform maintenance on the meter. If the customer plans to make modifications or additions which would render the metering facilities inaccessible, the customer must consult with Hawaiian Electric before making such modifications or additions, and make arrangements satisfactory to the utility for continued access by its workers.
7. What are the requirements for execution of the NEM agreement?
For qualified renewable energy generation systems less than 10 kW:
The Appendix I must be completely filled out with the customer information including the customer's name, address, electric account number, and contact information provided. The agreement must be signed by both the customer and the licensed electrical contractor who completed the work. The make, model and number of renewable generator (PV modules, wind turbine, hydroelectric generator, or biomass generator) and inverter information must also be provided. For more information on how to fill-out the NEM agreement, you can download a sample here.
A single line drawing accurately illustrating how power output from the renewable energy generator is interconnected to the utility is also required. A sample single line drawing can be downloaded here.
A lockable utility disconnect must be installed within close proximity of the meter.
The County in your area (City & County of Honolulu for Oahu) must have inspected the renewable energy generation system and closed the permits for the installation. Please call Hawaiian Electric Company at 543-4760 to inform us when your permit has been closed.
For qualified renewable energy systems greater than 10 kW but not more than 100 kW:
For systems greater than 10 kW and less than 30 kW, submit a single line drawing accurately illustrating how the system is interconnected to the utility along with relay list, trip, and settings of the generating facility. For system greater than 30 kW but not more than 100 kW, submit a three line drawing with a licensed professional electrical engineer stamp along with relay list, trip, and settings of the generating facility.
A certificate of insurance as described in section 6 of the NEM agreement is also required.
A lockable utility disconnect must be installed within close proximity of the meter or the electrical room.
The County (City & County of Honolulu) must have inspected the renewable energy generation system and closed the permits for the installation. Please call Hawaiian Electric Company at 543-4760 to inform us when your permit has been closed.
Call the contractor who installed your renewable energy generation system and have the contractor schedule an appointment with the electrical and building inspectors. The licensed electrician who completed the work needs to be present during the inspection. Closure of the building permit signifies that your system has been inspected and found to be designed and installed in conformance with applicable codes for safe operation. Final inspection and approval by both the building and electrical inspectors are required and are a vital part of executing a NEM agreement.
In accordance with Rule 18 of the tariffs, the utility will not execute a NEM agreement without approvals and closure of applicable permits. Please check with your County permit office to determine the status of your permits. On Oahu, you can review the status of your permit by accessing the Honolulu Department of Planning and Permitting website.
Enter your address or permit number on the form and click “GO” to search the permit database for the status of all permits on this site. Please call your utility to inform them when your inspection has been completed and the permit has been closed
9. What happens to my electric bill if I generate more electricity than I use from the utility?
Billing is on a monthly basis and you are responsible for a minimum charge even if you export more electricity than you take from the utility. The minimum charge covers some of the fixed costs of maintaining your electric account, including reading your meter and billing.
The NEM agreement allows the customer to carry over unused credits (excess net generation expressed as a monetary value) to future bills within a 12 month period, starting from when the agreement is executed. Unused credits left at the end of each 12- month reconciliation period may not be carried over to the next 12-month period.
In general, for systems up to 10 kW, you will need to enter into a simple NEM agreement with the utility which may be completed after your renewable energy generation system has been installed. Your contractor or electrician must obtain a building permit and have a licensed electrical contractor sign and certify your renewable energy generation system meets the necessary safety standards. NEM application processes for HELCO and MECO may differ; please check Hawaii Electric Light Company's website, or Maui Electric's website for details.
The building and electrical inspectors from the County office on your island will conduct an inspection to verify your renewable energy generation system meets required safety standards and they will proceed to close the building permit accordingly. See question 8 above for more information.
For systems over 10 kW up to 100 kW, the utility will perform an interconnection review. Unless more detailed study is needed, this review will be at no charge. It is highly recommended that you contact your utility early in your planning process to determine if they can accommodate the additional electrical loads from your renewable energy generation system. Any additional costs for facilities needed to complete the interconnection review will be the responsibility of the customer.
Also for systems over 10 kW but not more than 100 kW, you must enter into a more detailed customer agreement (see question 8 under download Rule 18 – Net Energy Metering Appendix II) that specifies the technical requirements necessary to ensure your renewable energy generation system can safely be connected to the utility grid. You will also need to provide proof of a commercial general liability insurance policy. The agreement must be signed by the licensed electrical contractor who installed your renewable energy generation system to certify that your renewable energy generation system meets the necessary safety standards and that an electrical permit was issued.
For photovoltaic energy generation systems up to 100 kW, the interconnection process is more streamlined especially if your system has an approved DC-AC inverter and PV Modules.
11. Why are interconnection requirements necessary?
If your renewable energy generation system mistakenly back-feeds power into an electric line that utility crews think is de-energized, the crews can be seriously injured or even killed. The interconnection study also helps assure the utility that you and other customers continue to receive reliable service and good power quality, avoiding potentially disruptive swings in voltage levels that could damage your equipment and that of the utilities.
Whether you are installing a new renewable energy generation system or considering NEM for an existing renewable energy generation system, compliance with all safety and other codes are required.
If you are an existing NEM customer (with an executed NEM agreement) and want to increase your generating capacity, you must complete the Addendum to existing NEM agreement and mail it back to HECO within 30 days.
The 2005 Legislature, by Act 104, gave the Hawaii Public Utilities Commission authority to set requirements and limits as well as safety, performance, and reliability standards for NEM by order, tariff, or rule.
15. Why does my bill not match my inverter(s) output?
Net Energy Metering is intended to offset part or all of customer's electric consumption from the Utility. During sunny days with low household consumption a customer's PV system may generate more electricity than used by the customer. Under these conditions the excess will flow back through the Utility meter to the grid. On other days a customer's PV system may not generate enough electricity to completely power the customer's load. In this case some electricity will flow from the grid through the Utility meter to supply the remaining power for the customer. Only the electricity flowing to and from the grid is measured by the Utility meter. The Utility meter will not measure the electricity generated by the customer's PV system to the customer's load. The Utility meter will only measure the excess electricity going back to the grid or the extra power supplied from the grid. Therefore, the energy measured by the Utility meter will not match the energy measured by the PV inverters. See PV system diagram below..